Scientists, Hydrogeologists, Soil Scientist, and Environmental Education
Specialists Located in
Drip Irrigation - New Technology for On-lot Disposal in Pennsylvania
8.0 Alternative Drip Irrigation System
A drip irrigation system is a type of micro irrigation system. The system is operated to operated to maximize the amount of unsaturated flow. This is accomplished by frequent, low-pressure applications of the treated wastewater within the biologically active zone. Under unsaturated flow conditions, there is improved renovation, detention, and aeration of the wastewater.
8.1 Siting Requirements
(a) The soils must be classified as either well drained or moderately well drained by a qualified soil scientist. The soil scientist will also determine the soil linear load , installation depth, tubing spacing, and minimum length of the drip field. The drip field area should avoid areas that are impacted by surface runoff, such as: swales, ditches, and gullies. A soil scientist is not required for large volume systems when the permit will be issued by the state.
(b) Percolation testing is not required, unless the soil scientist determines a test is necessary to confirm the soil classification. When percolation testing is conducted, the percolation rate must range between 3 and 90 minutes per inch in each drip zone. When percolation testing is conducted, a minimum of three percolation holes (see Chapter 73,Section 73.15) per zone are required. At a minimum, two drip zones are required.
(c) Slope in each drip irrigation zone must be between 0% and 25 %.
(d) The depth to seasonal high water table or a soil condition that results in a slower permeability (i.e., fragipan horizon) from the surface of the ground must be at least 20 inches. If this condition is meet, the drip tubing needs to be installed at least 6 inches below the ground surface and a maximum installation depth of 12 inches.
(e) The depth to a high permeable material or fractured rock 26 to 32 inches depending on the installation depth. If this condition is meet, the drip tubing needs to be installed at least 6 inches below the ground surface and a maximum installation depth of 12 inches. This is because the minimum separation between the bottom of the drip tubing and the limiting zone is 20 inches.
8.2 Treatment Requirements
Prior to disposal, via drip irrigation, the wastewater must be pretreated using the following pretreatment system:
(a) Septic tank or aerobic treatments.
(b) Intermittent sand Filtration using buried or free access sand filters.
(c) Final filtration using a hydraulic unit fitted with in-line disk filters meeting or exceeding the filtration achieved by the "American Septic Drip" system disc filters. The system requires an automatic backwash system. All backwashing must be returned to the first septic tank or inlet of an aerobic treatment tank.
My professional recommendation typically includes the following: initial waste segregation to increase the removal of grease and oils, dual compartment septic tanks to increase solids reduction, aerobic treatment unit, Zabel effluent filter, free access sand filters, and appropriate hydraulic pumping/filtering system. The combination of septic and aerobic treatment provides for increased solids retention, decreases the effect of shock loads, provides a continuous source of carbon to aerobic unit, and provides a degree of safety if there is a problem with the aerobic unit. A Zabel filter or the equivalent is recommended to decrease the particle load to the free access sand filters.
Only approved drip manufacturer in Pennsylvania is American Manufacturing Company, 5517 Wellington Road, Gainesville, Virginia, 20155, 1-800-345-3132 please inform them that you reviewed the information online at this website.
Conventional Spray Irrigation
, Low Volume Spray Irrigation, and
Individual Residential Spray Irrigation Systems.
More Links on Drip Irrigation
To obtain more information about the company and its services,
please E-mail: B.F. Environmental.
It would be appreciated if you would put your name, company name, mailing address, and phone number in the message.
Online Internet Business Directory